Joined: 10 Mar 00
This post is more of a solution looking for a problem...
I noticed in the technical news that there was trouble with the data cables for the UPSs.
If these are APC Smart-UPS UPSs, as the technical news seemed to suggest, I may have a solution to the problem, having had the same problem myself.
When one type of data cable is used with these UPSs - i.e.: USB or serial - the UPS will no longer respond via the other type of cable until the UPS is reset. This may be achieved as per instructions I received from APC support:
1) Turn the UPS OFF.
2) Disconnect the USB / Serial cable.
3) Disconnect the mains power cable.
4) Hold the test button down for 5 seconds.
You should hear a click.
At this point, either type of cable should be useable until one type has been used.
I hope this helps and is relevant.
©2017 University of California
SETI@home and Astropulse are funded by grants from the National Science Foundation, NASA, and donations from SETI@home volunteers. AstroPulse is funded in part by the NSF through grant AST-0307956.